Absorption Distance In Action
In the last couple Monday Morning Minutes, we showed how the type of humidifier dispersion method could affect the absorption distance. Let’s look at an example.
Ex: 5000 CFM at 55OF Duct temperature to provide a room RH at 35% at 70OF with 50% outside air.
- Traditional single tube dispersion……… 59” inches absorption
- Rapidsorb multiple tube dispersion..….. 22” inches absorption
- Ultrasorb panel type dispersion………… 6” inches absorption
As you can see, in tight spaces, Ultrasorb or Rapidsorb can solve wetting problems in ducts.
Next week, we’ll look at how to save energy.
Disclaimer: R. L. Deppmann and it’s affiliates can not be held liable for issues caused by use of the information on this page. While the information comes from many years of experience and can be a valuable tool, it may not take into account special circumstances in your system and we therefore can not take responsibility for actions that result from this information. Please feel free to contact us if you do have any questions.