Last week the article covered pressure drop correction calculations. Today we offer you some handy charts to use for second glycol correction pressure drop. Example: I have calculated the water piping pressure drop through a chilled water system to be 80 feet using the System Syzer. Question: What is the pressure drop if I have 50% Ethylene Glycol/Water with temperatures of 45°F to 55°F? Answer: The average temperature is 50°F, so my factor is 1.47. [Read more…]... READ MORE
Question: I have selected my piping friction loss based on water, but I am pumping a glycol solution. What correction do I use? Answer: There are three glycol corrections when designing a hydronic or process cooling system; heat transfer correction, pressure drop correction, and pump curve correction. This R L Deppmann Monday Morning Minute defines the second of three glycol corrections. [Read more…]... READ MORE
An engineer in Michigan called about a large project with several pumps being selected in parallel for a plant chilled water system. He commented that... READ MORE
Norm Hall, R.L. Deppmann and Chad Edmondson, J. M. Pleasants
/
July 18, 2016
When looking at Bell and Gossett pump selections, we often find higher part load efficiency (PLEV) pump choices are to the right of the BEP, or best... READ MORE
R. L. Deppmann Company Monday Morning Minutes addressed corrections to system GPM (gallons per minute) and system friction head during the last three weeks. Today we look at the pump selection. Centrifugal pump curves and the brake horsepower required changes depending on the fluid. In HVAC design we normally assume water is the pumped fluid. There are many times when the assumption is water, since there is no fluid mentioned on the schedule, yet we find a glycol makeup unit attached to the system. [Read more…]... READ MORE
Pump curves are based on water, but I am pumping a glycol solution. How will this affect the selection? This week we define the first of three glycol corrections. There are three glycol corrections when designing a hydronic or process cooling system; heat transfer correction, pressure drop correction, & pump curve correction. The first correction we’ll look at is heat transfer correction. When choosing chillers, boilers, heat exchangers, and terminal units, it is important to select them using the correct system fluid. [Read more…]... READ MORE
Centrifugal pumps are the “heart” of hydronic heating, cooling, and plumbing systems. Over the next few weeks, the R. L. Deppmann Monday Morning Minutes features some basic and advanced pumping topics. Let’s start with a quick review of the information contained on the pump curve. For our example, we will use an ITT Bell and Gossett model 1510 end suction base mounted centrifugal pump model 5E with a nominal speed of 1750 RPM. The horizontal axis is flow rate in GPM or gallons per minute of water. [Read more…]... READ MORE