## Glycol Pressure Drop Corrections for Hydronic Systems (Part 2)

Norm Hall

Last week the article covered pressure drop correction calculations. Today we offer you some handy charts to use for second glycol correction pressure drop. Example: I have calculated the water piping pressure drop through a chilled water system to be 80 feet using the System Syzer. Question: What is the pressure drop if I have 50% Ethylene Glycol/Water with temperatures of 45°F to 55°F? Answer: The average temperature is 50°F, so my factor is 1.47. [Read more…]

## Pressure Drop Corrections for Glycol in HVAC Systems (Part 1)

Norm Hall

Question: I have selected my piping friction loss based on water, but I am pumping a glycol solution. What correction do I use? Answer: There are three glycol corrections when designing a hydronic or process cooling system; heat transfer correction, pressure drop correction, and pump curve correction. This R L Deppmann Monday Morning Minute defines the second of three glycol corrections. [Read more…]

## Glycol in for HVAC Systems (Part 3) – Pump Corrections

Norm Hall

R. L. Deppmann Company Monday Morning Minutes addressed corrections to system GPM (gallons per minute) and system friction head during the last three weeks. Today we look at the pump selection. Centrifugal pump curves and the brake horsepower required changes depending on the fluid. In HVAC design we normally assume water is the pumped fluid. There are many times when the assumption is water, since there is no fluid mentioned on the schedule, yet we find a glycol makeup unit attached to the system.

## Centrifugal Pump Curve Corrections for Glycol in for HVAC Systems

Norm Hall

Pump curves are based on water, but I am pumping a glycol solution. How will this affect the selection? This week we define the first of three glycol corrections. There are three glycol corrections when designing a hydronic or process cooling system; heat transfer correction, pressure drop correction, & pump curve correction. The first correction we’ll look at is heat transfer correction. When choosing chillers, boilers, heat exchangers, and terminal units, it is important to select them using the correct system fluid. [Read more…]

## The Bell and Gossett System Syzer® – a few other uses

Norm Hall

Printer Friendly (PDF) In the last two MMM articles we used examples of pipe selection for water and other fluids. Using the electronic version of …